Tecumseh 5-1/2 Ton 230 Volts (3-Phase) 68,000 BtuH (R-22)
Quantity in Basket: None
5-1/2 Ton OEM Tecumseh Air Conditioning Compressor:
Replaces Part Numbers:
AGA5568EXT, AG144RT-001-A4Y, PY7766HF, 48HD007, 38AFP007, WY7260AA, 06RC148500, 06RM248581, 50SR661420, 685347-36, AG5568E, P031-6851, AG144RT-001-J7, CARAGA5568EXT, CARB92754.
Suction Tube ID: 7/8"
Discharge Tube ID: 1/2"
Used in Carrier, Bryant, Payne Air Conditioning Models:
50DJ014510 0038 48DJE007520 0037 38BA005520 0021 50VQK080FMC5 0014 50VQK080FMN5 0014 50VQK160FMC5 0014 50VQK160FMN5 0014 48LJD007500 0038 48LJE007500 0038 50DJ007500 0027 50DJ007510 0027 48DJD007500 0038 48DJD007510 0038 48LJD007520 0040 50LJ007500 0030 50LJ007503 0030 50LJ007803 0030 50VQD080FMC5 0014 50VQD080FMN5 0014 580CPV072074AA 0038 580CPV072115AA 0038 50DJ007520 0031 50VQD160FMC5 0014 50VQD160FMN5 0014 50LJ007520 0034 558CPX072000AA 0030 558CPX072000JA 0030 558CQX072000JA 0030 48LJE007520 0040 558CPX072000AC 0034 50VQN160FMC5 0014 50VQN160FMN5 0014 48DJD014500 0035 48DJD014510 0035 48DJE007500 0038 48HD007500 0035 48DJE007510 0038 48HD007510 0035 48HD 007520 0035 48HD 007530 0035 50LJ014500 0035 48HD007540 0035 48HD007550 0035 580CPV150220AA 0040 48LJD014500 0040 50VQA080FMC5 0014 50VQA080FMN5 0014 580BPV072074AA 0038 580BPV072074AB 0038 48DJD007520 0037 580CPV072074AC 0042 580BPV072115AA 0038 50VQA160FMC5 0014 580BPV072115AB 0038 580CPV072115AC 0042 50VQA160FMN5 0014 558CPX150000AA 0035 50DJ014500 0038
Below are some common questions about our compressors.
If you have a question that is not addressed below, please send us an e-mail attention *parts departmaent*.
What oil is used in an R-12 compressor manufactured today? Synthetic alkylate.
What is synthetic alkylate oil? Synthetic alkylate is another name for alkylbenzene, which is used in many of our hermetic compressors.
Is 3GS mineral oil compatible with "white oil" and alkylbenzene oil? Yes.
They have different properties, but are chemically compatible.
How long may I leave a compressor charged with POE oil open to the atmosphere? No more than 15 minutes maximum.
Can blends be charged as vapor? No.
Blends must be charged in liquid phase.
Can R-410A be used in a compressor designed for R-22? No.
Tecumseh is currently developing a line of R-410A compressors.
What is the highest acceptable motor winding temperature for your hermetic motors? 265 degrees Fahrenheit, measured by the resistance method, is the highest acceptable temperature for our hermetic motors.
At what speed do your hermetic compressors run? Our 60 Hz. compressors run at a nominal 3450 rpms at rated voltage, and our 50 Hz. compressors run at 2,875 rpms.
Can I use a "one size fits all" type of start relay on all of your hermetic air conditioning compressors? No. Tecumseh Engineering department has selected specific relays for each compressor to meet there starting specifications. I don't have the correct voltage rating on a run capacitor, as specified in your literature; can I use a different voltage rating? Yes. The voltage rating of all capacitors must be the same as, or greater than, the specified voltage. If I am replacing a failed compressor with a like new compressor can I use the electrical components from the old compressor on the new compressor? You should use only new electrical components (e.g. relay, start capacitor, run capacitor) designed for use with the new compressor. Is it safe to use leak detection dyes in air conditioning and refrigeration systems? Tecumseh Products Company does not endorse the use of any substance in the system except the oil and refrigerant designed for use in the specific compressor. Do your capacitors contain PCB oil? Since January 1979, capacitors provided by Tecumseh have contained non-PCB oils. Do your compressors contain PCB's? No. Do you have a mathematical equation and coefficients for your compressors' performance data? Yes. We publish compressor performance information to our OEM's in the ARI Standard 540 format. In air conditioning applications, how does horsepower compare to Bth/hr.? At air conditioning rating conditions one horsepower equals 12,000 Btu/hr. Can I use my own grommets on your compressors? Yes, if they pass your system shipping/transportation and sound/vibration tests. What is "D21"? Discharge temperature measured with an insulated T/C two inches from the compressor tube to line joint. Why can't I move the electrical warning label or bar code labels? Readers or scanners in production are fixed and changing would have to be agreed upon by all customers. Safety reasons govern changing electrical label.