Furnace Ignition Control Module ( Johnson Controls, Lennox Furnaces) *UPGRADED MODULE
Quantity in Basket: None
Johnson Controls, Lennox Ignition Control Module.
WHEN PLACING YOUR PARTS ORDER, YOU CAN ORDER ONLINE 24 HOURS A DAY OR BY CALLING OUR SALES CENTER MONDAY THROUGH FRIDAY 7AM TO 5PM PACIFIC TIME. WE WILL SHIP YOUR PART FROM THE CLOSEST WAREHOUSE PER YOUR ZIP CODE. WE CAN SHIP YOUR PARTS TO YOU NEXT DAY AIR, SECOND DAY AIR OR 3 DAY SELECT OR U.S. POST OFFICE, AND WHEN PLACING YOUR ORDER ONLINE SHIPPING ESTIMATES WILL BE PROVIDED TO YOU FOR EACH SHIPPING CLASS.
New Upgraded Ignition Module is a universal replacement part for intermittent pilot controls.
The G776 ignition control kit can only be used to replace a Lennox G20, G20R, G23, and G26 series unit that has a Johnson Controls G776RGD-1, G776RGD-2, G776RGD-10, or G776RGD-11 ignition control installed; or has been replaced with a Lennox 65K93 ignition replacement kit.
Replaces Ignition Control Part Numbers:
BG1600M02CJ-1AA CARBG1600M02CJ-1AA G776RGD-10 G776RGD2 G776RGD10 G776RGD11 G776RGD-1 G776RGD-2 65K93 G776RGD-10 G776RGD-11 G776RGO-11 G776RGO11 G776RG0-11 G776RG011 G776RGD-14 CAR65K93 CARG776RGD11 CARL38956 CARG776RGD14.CARBG1600M02CR-1ADC.
Used in Lennox Furnace Models:
G23Q4/5-100-2 G23Q45-100-2 G23Q451002 G23Q2/3-75-1 G23Q2/3751 G23Q23751 G20R G26Q3-75-1 G20R03/4E100-8 623Q3/4-100-4 G23Q3/4-100-4 G2303/4-125-2 G776RGD-10 G23Q2/3-75-2 G23Q2/3-75 G776RGD-1 G201 G20Q3/4E-100-5 CG20Q3E-75-1 G200 G20R G231 G230 G261 G260 G16RQ4-100-9 G16RQ41009 G776RGD-2 G776RGD-10 G776RGD-11
Use only to replace Lennox G20, G20R, G23 and G26 series unit that has a Johnson Controls 69J3601, G776RGD-1, G776RGD-2, G776RGD-10, G776RGD-14C or G776RGD-11 ingintion control installed : or has been replaced with a Lennox 65K93 ignition replacement kit
G779 Universal Replacement Intermittent Pilot Ignition Control
Operating Voltage 24 VAC at 50/60 Hz
Operating Current 25 VAC, 60 Hz
Contact Rating (PV & MV) 2 A continuous, 5 A inrush
Operating Temperature -40° to 160° F
Humidity Rating 95% RH @ maximum operating temperature non-condensing
Ignition Source High voltage spark, capacitive discharge
Prepurge Less than one second
Number of Trials Before 100% Shutoff One
Trial Time for Ignition 25 seconds (a)
(a) Timings increase by 20% under 50 Hz operation
Retry Delay Period 5 minutes (a)
Recommended Spark Gap 0.125 inch maximum
Means of Flame Detection Flame rectification
Flame Failure Response Time 0.8 seconds
Minimum Flame Current Required 0.15 mA
Wiring Connections Spark: Spike
Control: 1/4 inch male spade
Type of Gas Natural, Liquified Petroleum (LP), manufactured, mixed or LP gas-air mix
This New Upgraded Ignition Module can be used with all gases and applicable to gas-fired appliance with maximum 400,000 BtuH. This module has a seperate spark / sense only will operate without vent dampers. Module Specifications:24 VAC 50/60 Hz, 0.2A nominal and main valve. 100% Pilot Shutoff if pilot is not proven;after 5 minute delay.15 seconds prepurge.
Perform the following procedure to replace the existing ignition control
Only a trained service professional should perform this procedure.
1. Shut off power to the appliance.
2. Turn off the gas at the manual shutoff valve adjacent to the appliance.
3. Label each wire with the correct terminal designation prior to disconnection.
4. Disconnect the power supply (transformer) and the thermostat lead wires from the existing ignition control.
5. Disconnect the sensing probe lead, the high voltage cable, the pilot valve and main valve leads, and any ground leads from the existing ignition control.
6. Remove the screws holding the ignition control assembly in place.
7. Remove and discard the ignition control.
8. Using the same holes as the old control, mount the new control with metal screws or bolts through the mounting holes of the enclosure.